Home Farm Water Treatment Plant
Our new water treatment plant facility has now been in full operational status since the early part of October 2018. The $12 million dollar project started construction in July 17, 2017 which involved building a biological manganese filtration facility while keeping the existing plant on line until completion. Also six of our eight groundwater supply wells were refurbished with the new pumps, motors and motor control centers to match the new pump head conditions.
Testing began in early September and approximately forty (40) percent of the total daily flow began being pumped out to the system in late September with the remainder being supplied by the old facility. Since early October all system water has been processed through the new plant.
The treatment plant uses a treatment process developed in Europe by Suez Water Technologies and Solutions, a subsidiary of Suez Water which is the largest water company in the world. The treatment process utilizes the newest generation of manganese removal filtration which encompasses a greener more environmentally sustainable methodology to biologically remove the manganese than the conventional treatment methods used extensively by water utilities of chemically precipitating out the manganese. This process also allows for higher flow and filtration rates and longer run times between backwashes to improve water quality.
After partial acclimation with the biological manganese biomass in a three week period, we were at 0.0 ppm of manganese entering the system and continue to remain at that level. Representative samples taken throughout the system weekly confirm that manganese levels are at zero or near zero at all sites.
The distribution system of existing water main and services has older buildup of manganese of varying degrees depending on the type of pipe and location in the system. As we change the biological and chemical composition of the finished water, the existing manganese inside the pipes will start to break up and dissipate as the pipe environment changes. This situation is expected and can cause temporary discolored water as the system readjusts. In early spring weather permitting, the Department will be conducting hydrant flushing to remove existing manganese and sediment. The process will be repeated again in the fall. It will take a period of time to clean out and remove remaining pipe deposits but conditions should steadily improve between the treatment removal process and flushing of the distribution system.
As part of the new treatment process, we are running what is known as a double barrier contact time process to protect against potential viruses and pathogens. This process is intended to be run as a log-four removal (99.99) percent which involves keeping chlorine residual of 0.4 ppm. The previous plant used chlorine gas as a disinfectant and with insoluble manganese that could not be sequestered entering the system, the chlorine would bind to the manganese. Now with the manganese component removed along with a higher chlorine, the chlorine is working more freely throughout the system. Customers that experience a strong chlorine taste or odor in the water are actually encountering a level of chlorine that is too low as it is being used by organic matter bound up by the existing manganese and a small amount of iron in the pipelines. As the demand is used up and a free chlorine residual of at least 0.1 ppm is established furthermore, any strong chlorine tastes or odors should dissipate. We are gradually adjusting our levels of chlorine to reach this free chlorine system residual which is known as break point chlorination. We thank all our customers for their patience and understanding as we implement these changes into our treatment process to achieve our overall goal of improved and consistent water quality throughout the Town.
Shrewsbury Completes Solar Array at Home Farm Water Treatment Plant
In a ceremony in Ware, April 2018, the Baker-Polito Administration, though MassDEP’s Clean Energy Results Program, with support from the Department of Energy Resources and the Massachusetts Clean Energy Center, awarded $4 million in state Gap II grants to Water and Wastewater Facilities for energy efficiency projects and renewable power generation in the Commonwealth.
The Town of Shrewsbury secured a $200,000 State Gap II Grant, which was combined with $27,525.00 in local funds, to complete the design and construction of a 59.2 kW ground mounted solar array to help offset electricity costs associated with a new Water Treatment Plant at 45 Main Street. The Town hired Solar Design Associates to design the solar array and Ostrow Electric to construct it. The Town is pleased to report that the project was completed in the spring of 2020 and the array is now online.
Since going online, the array has generated 22,000 kWh of energy and avoided 33,000 lbs of carbon emission into the atmosphere.
Real time data can be viewed at: http://das.solardesign.com/gcdash.php?site=ShrewsburyWaterTreatment
General Customer Service - All General Questions
Phone: 508-841-8502 Prompt #6
Solid Waste- All Trash and Recycling Needs
Phone: 508-841-8502 Prompt #1
Utility Account Management- Billing Questions, Final Water Reads, and Meter Replacements
Phone: 508-841-8502 Prompt #2
Permitting- Construction, Highway Trench, Driveway, Drain Layer
Phone: 508-841-8502 Prompt# 3
Procurement- Contracts and Public buildings
Phone: 508-841-8502 Prompt # 4
A/P & Payroll- Invoices, Billing, Weights and Measures
Phone: 508-841-8502 Prompt # 5